Item description Electric Heat Sequencer / Motor Fan Blower Control 2-DPST-SPST 24 Volt for Q107 / 24A34-14 / 525-37328-000. McCombs Supply. Fast Shipping. Est 1953.
Parts Connect Sequencer part number PCQ107.
2 DPST-1 SPST Sequencers
1 Timing / 1 Switch
Off 1-160 Seconds
On 1-160 Seconds
PSQ Models are Direct Replacement for Most Fan / Heat Sequencing Functions.
Terminal Markings are Equivalent to Competitive Types.
Replacement for Numbers:
Diversitech DGS107, Honeywell R8330D1039, Klixon 51172-131-5, Mars 33848, Napco NS107, Robertshaw 611-007, Supco Q107, White Rodgers 24A34-14, York 525-37328-000.
COMBINED LOAD RATING TABLE
30A @ 240 VAC TOTAL,
23A Non-Inductive + 7 FLA
/ 42 LRA
ON Time: Elapsed time to make contacts after
heater is energized (min. to max.)
OFF Time: Elapsed time to break contacts after
heater is de-energized (min. to max.)
M1-M2 and M3-M4 are always first switches
to turn ON and last to turn OFF. All other
switches are random ON and random OFF
: Underwriters Laboratories requires a
fan interlock circuit to insure the blower
remains operating whenever more than one
sequencer is used.
The fan interlock should
be the M1/ M2
contacts of the second or third sequencer.
All M1/ M2
contacts are wired to the blower
motor so that any sequencer that is energized
will keep the blower ON.
What organisations does mccombssupply.com support?
mccombssupply.com supports earthday.org see how here
Charities description: Visit the official Earth Day site to learn about the world's largest environmental movement and what you can do to make every day Earth Day.
Reviews of Electric heat sequencer / motor fan blower control - PCQ107
Sorry there seems to be no average rating yet in our system for the Electric heat sequencer / motor fan blower control - PCQ107
electric heat sequencer / motor fan blower control buyers from mccombssupply.com say... "Bought this Parts Connect Sequencer part number PCQ107.One I had after month was burn out on two parts .So far have had this one in works great .Easy to install ."